End-to-End Data Center Crash Test!
Elite 3rd party, vendor independent data center testing & data center commissioning units that mobilize and camp on data center site, running rigorous test scripts, using sophisticated equipment and tools, that test and commission every component of the data center with absolute know-how of exact approach to commission a site which is fault-tolerant, fail-safe and reliable for live operation.
Experts will run through the design criteria of the data center and based on this create sophisticated test scripts which will ensure that the final operations of the data center facilities is meeting the business objectives of the design. Full loading on gradual applied load-incline methods will be applied to the data center and every aspect ranging from performance to redundancy will be undergoing rigorous tests. A site is not operational or at least not availability-safe unless it passes through our testing and commissioning processes and receives full acceptance on individual functioning systems as well as the fully integrated site test results. The following are the TechXact’s testing and commissioning process methods:
Individual System Functional Site Test
Functional site test to 2N, N+1 one leg at a time, fault disturbance and monitoring for a period trending, switchboard site point-to-point, main, sub, busbars measurement, SI, protection relay, ACB direct acting, earth loop impedance, PDU testing and verification, load testing, noise test, UPS, earthing grids, signal reference grid, visual inspections, etc.
Fully Integrated Level-5 Test & Commissioning
Fully integrated functional tests will be used to prove the functionality of the data center against its design parameters. The service will stress test the data center environment and full functional tests scripts will be used to ensure that the redundancy and capacity is meeting the design specs and business needs.
Individual System Site Acceptance Test
Mains supply resilience, PQM, UPS on DC heater load, ATS operations, generators synchronization test, alarms activation, smoke detection simulation, gas activation in stages, room integrity testing, and other such integral testing components must all pass successfully to complete a full site acceptance test.
Testing & Commissioning Report
Providing full detailed test scripts, commissioning guides, reports of all conducted testing and commissioning, O&M checks, performance benchmarking, competency report, error reports, critical malfunction reports, design vs buildup misalignment reports and such related report documentation are necessary to effectively record and conclude all testing activities.